It has been identified that some customers are experiencing failures of the 4-20mA circuit in our discrete EL relays. The fault has no impact on the relay’s trip function capability, which remains fully functional as designed. The fault is unveiled as an incorrect 4-20mA output regulation. The 4-20mA output is provided for remote monitoring of the effective EL current being detected by the relay.
Ampcontrol has received reports of a customer experiencing nuisance EFLO trips on new IPD 11kV EFLO equipment. Upon inspection of hardware and investigation, Ampcontrol was able to identify that the environmental conditions subjected to the hardware as the root cause of the nuisance tripping.
The ELV-PRO relay is a successor to the VSD-Guard, a premium Earth Leakage Relay providing users with a greater visibility and insight into the earth leakage currents within their system. In recent months a number of concerns have been raised regarding the relay experiencing nuisance tripping. The concerns identified with the product do not prevent the ELV-PRO detecting Earth Leakage faults; rather users may experience nuisance tripping. The relay does not present a safety risk with all trips / failures resulting in a safe failure condition.
The function of the earth continuity system is to enable SAFE and RELIABLE operation of reticulated mining equipment by ensuring the presence of an adequate earth connection. Earth continuity is typically required in applications where there is a fundamental reliance on the earth return impedance for the electrical safety of the operating equipment.
Ampcontrol have been contracted as the sole supplier for a large resources tunnelling project and are set to deliver a range of equipment, cable and maintenance services throughout the construction phase of the project.
Designed to supply power to tunnel surface operations including a welding factory, the containerised substation developed by Ampcontrol will act as the main distribution system on-site.
IPD to OCS protection system feature differences.
Ampcontrol’s customer in Turkey specialises in the mining, processing, distribution and importation of hard coal. Working in partnership with the customer, Ampcontrol carried out the
commissioning of a AW2000/E7/B 1100/500V circuit breaker.
Ampcontrol has recently been made aware of a condition that causes the ELD V3 and ELV V2 relays to power up into a tripped state. The trip is related to the internal charge of the super-capacitor. The issue may cause delayed power up of equipment as a reset will be required if a trip occurs.
The cause of this trip is not a safety concern nor will it pose any risks to operations experiencing this condition. The trip was detected during the commissioning stage where the equipment was undergoing repetitive power cycles.
The Ampcontrol Outlet Test System (OTS) provides a fully automated outlet testing facility. The OTS completely eliminates paper-based record keeping by concurrently updating a historical database with the latest test data.
The OTS is comprised of an OTS module, embedded within the outlet electrics, and an OTS Comms Module, mounted on the door to provide Bluetooth connectivity to the outlet tester.
All tests are initiated wirelessly via the OTS Application Software, which is installed on compatible Bluetooth enabled devices. Each outlet is able to be individually targeted.
All local test records are managed within the OTS Application Software until the tablet performs an authorised sync with the AWARE cloud storage. When this occurs all local test reports are uploaded to the cloud, and then all Assets and Users are refreshed for selected site. All OTS test records can be accessed by anyone with internet access and authorisation (user account).
The Ampcontrol Outlet Test System – Earth Leakage (OTS-EL) provides a fully automated outlet earth leakage testing facility. The OTS-EL completely eliminates paper-based record keeping by concurrently updating a historical database with the latest test data.
The OTS-EL is comprised of an OTS-EL module, embedded within the outlet electrics, and an OTS Comms Module, mounted on the door to provide Bluetooth connectivity to the outlet tester.